Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Available Fuel: Nature gas, coke oven gas, biogas, methanol, liquid propane gas, diesel, heavy oil, light oil, crude oil, etc.
Available Industries: Heat supplying, chemical, food, textile, printing and dyeing, cigarettes and tobacco, fodder, pharmacy, building materials, brewery, rubber, hospital etc.
WNS series horizontal internal combustion boiler is a boiler shell type 3 passes wetback oil/gas fired boiler. After fuel is being atomized by burner, flame is full of the wave furnace and transfer heat via furnace wall, this is 1st pass; the high temperature smoke is collected in reversal chamber and then enters 2nd pass which is grooved tubes bundle area; after heat convection, air temperature gradually falls and goes to front smoke box and turn to 3rd pass, which is smooth tubes bundle area, and then enters chimney passing back smoke box and exhausted to the atmosphere.
1. Digitized manufacture
The key part such as material cutting, rolling, drilling are proceeded by advanced CNC machining process to reduce the assemble stress and extend boiler working lifetime.
The front and back smoke chamber plates are cut by CNC plasma cutting machine and looks tidy and beautiful.
2.Easy operation and maintenance
Fully automatically operating, with automatically adjustment and protection of burning, water level, temperature and steam pressure.
3. Longer working life
Smoke tube and tube sheet connection is expanded first to eliminate the gap between them, then adopt automatic argon arc welding to relief the stress and expand boilers working life.
Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will have 100% radiographic inspection.
Fin tube us ND steel or stainless-steel material which avoid low temperature corrosion.
Inspection procedure point is set up to guarantee the sequence of expanding and welding, avoid cracking of the tube sheet holes.
4. Less fuel consumption
High quality aluminum silicate fiber is used with fire clay insulation, to control the boiler body temperature below 45℃ to control heat lost.
Sufficient steam storage room and heating area makes boiler to generate high quality steam and high thermal power.
Condenser is added to reuse the waste heat of the exhausted smoke to increase feeding water’s temperature and reduce emission temperature, which can increase the thermal efficiency above 98% and save operating cost.
Author: Ray Wohlfarth You should then close the main steam valve, main water feed vales, and main gas valve. Finally, turn off the circuit breaker. If you have any questions or concerns about turning your boiler on and off, or any other procedures, double check the owner’s manual.
Boiler controls help produce hot water or steam in a regulated, efficient, and safe manner. Combustion and operating controls regulate the rate of fuel use to meet the demand. The main operating control monitors hot water temperature or steam pressure and sends a signal to control the firing rate, the rate at which fuel and air enters the burner.
Per ASME standards, one NRV is required for one-boiler, high pressure applications (above 15 psig). For high-pressure applications involving multiple steam boilers with manholes that are connected to a common steam main, the steam connection from each boiler must be fitted with two stop valves.
Model 4A Part No.401413 Air Valve (non-vacuum) Float-type thermostatic vent For residential or small one-pipe or two-pipe systems Single non-adjustable port 1/2 NPT female and 3/4 NPT male straight shank Install 6-10″ (150-250mm) above horizontal return and 18″ (450mm) above the boiler water line Maximum operating pressure 2 psig (0.13 bar)* Maximum pressure 10 psigRead more
Sep 11, 2018· There are two types of steam stop valves are used in the boiler. 1. Main steam stop valve 2. Auxiliary steam stop valve A main steam stop valve is a valve usually connected directly to the boiler for the purpose of shutting off the steam from the
If you have boiler operator military experience and training and want to become licensed in Maine as a stationary steam engineer or boiler operator, please contact Catherine Carroll (207-624-8605) or email the office before submitting an application.
Jun 14, 2018· Measure from the ceiling down to the lowest steam carrying main. Deduct the measurement of the lowest steam carrying main from the water level measurement to acquire the “A” dimension. This “A” dimension should be a minimum of 28 inches. If not, the boiler could have operational problems and noises. Plan on re-piping the near boiler piping.
The steam lines are a critical components system in the boiler tower: in particular the main steam and hot reheat lines are made by thick pipes that are necessary to transfer the steam from the top of the boiler to the steam turbine room, generally located at ground level.
Your boiler may be oversized, and it is hard to correct that, however, you can let the air out as quickly as possible, using larger main vents. This will fill all the supply pipes first, before the steam begins to rise up to all the radiators simultaneously, making an even heating in all rooms.
Boiler Valves are integral parts in any steam or heated water applications. Boiler valves are used as safety equipment in steam boilers to control pressure & control temperatures. There are several types of steam boiler valves available in the market as per the requirement. Types of Valves Main types of boiler valves are as … Main Types of Steam Boiler Valves or Safety Valves Read More »
Normand marine steam boilers The main difference between the Normand marine steam boiler and the Yarrowboiler is the external downcomers. Nuclear marine steam boiler Nowadays marine nuclear marine steam boilers are used in large navy ships and icebreakers serving in Arctic waters
No. 76, Xin Da Road, Zhou tie Town, Yixing, Wuxi, China
0086-510-68530066, +86-13506151292Get Latest Price
Copyright © 2020.Zhongzheng Boiler Co., ltd. All rights reserved.