Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Available Fuel: Nature gas, coke oven gas, biogas, methanol, liquid propane gas, diesel, heavy oil, light oil, crude oil, etc.
Available Industries: Heat supplying, chemical, food, textile, printing and dyeing, cigarettes and tobacco, fodder, pharmacy, building materials, brewery, rubber, hospital etc.
WNS series horizontal internal combustion boiler is a boiler shell type 3 passes wetback oil/gas fired boiler. After fuel is being atomized by burner, flame is full of the wave furnace and transfer heat via furnace wall, this is 1st pass; the high temperature smoke is collected in reversal chamber and then enters 2nd pass which is grooved tubes bundle area; after heat convection, air temperature gradually falls and goes to front smoke box and turn to 3rd pass, which is smooth tubes bundle area, and then enters chimney passing back smoke box and exhausted to the atmosphere.
1. Digitized manufacture
The key part such as material cutting, rolling, drilling are proceeded by advanced CNC machining process to reduce the assemble stress and extend boiler working lifetime.
The front and back smoke chamber plates are cut by CNC plasma cutting machine and looks tidy and beautiful.
2.Easy operation and maintenance
Fully automatically operating, with automatically adjustment and protection of burning, water level, temperature and steam pressure.
3. Longer working life
Smoke tube and tube sheet connection is expanded first to eliminate the gap between them, then adopt automatic argon arc welding to relief the stress and expand boilers working life.
Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will have 100% radiographic inspection.
Fin tube us ND steel or stainless-steel material which avoid low temperature corrosion.
Inspection procedure point is set up to guarantee the sequence of expanding and welding, avoid cracking of the tube sheet holes.
4. Less fuel consumption
High quality aluminum silicate fiber is used with fire clay insulation, to control the boiler body temperature below 45℃ to control heat lost.
Sufficient steam storage room and heating area makes boiler to generate high quality steam and high thermal power.
Condenser is added to reuse the waste heat of the exhausted smoke to increase feeding water’s temperature and reduce emission temperature, which can increase the thermal efficiency above 98% and save operating cost.
Boiler uses this principle to produce high pressure steam. Conversion of Water to Steam evolves in three stages. Heating the water from cold condition to boiling point or saturation temperature – sensible heat addition. Water boils at saturation temperature to produce steam – Latent heat.addition. Heating steam from saturation temperature to higher temperature called Superheating to increase the power …
B&W's chemical and heat recovery boilers for the pulp and paper industry range from a pulp mill liquor processing capacity to 10,000,000 lb/day (4500 t/day) dry solids at steam pressures up to 1850 psi (12.6 MPa) with the PR design and to 2600 psi (17.9 MPa) with the reheat design.
The high pressure steam so generated is used to generate power. The boiler works on the same principle as the water is heated in a closed vessel and due to heating, the water changes into steam. Online Chat Email. introduction about steam boilers - flashpoints.au.
Jan 01, 2013· Power boilers are defined as boilers that generate steam at pressures in excess of 15 psig, for external use. Most designers and owners of steam-generation systems from fired heaters agree that ASME Code Section 1 is the appropriate design code for the steam system.
By this pipe generated steam passes through. There are two steam pipes in Locomotive Boiler. First one is the main steam passing pipe. It located between the superheater and dome. The second steam pipe is connecting the superheater exit end to the steam engine. Related: Construction and Working Principle of Scotch Marine Boiler
of boiler capacity. It is generally measured in tons or kg per hour. 21 Boiler Efficiency Efficiency of a boiler may be defined as the ratio of heat utilized for the generation of steam to heat supplied due to the burning of fuel. Boiler efficiency, ms be the mass of steam evaporated in a given time mf be the mass of fuel burnt at the same time HV
Turbines - an overview | ScienceDirect TopicsFeb 01, 2010Condenser Pressure - an overview | ScienceDirect Topics Pressure Steam - an overview | ScienceDirect Topics See more results Control steam usage to ensure that steam demand does not exceed boiler capacity. Control changes in steam usage to ensure that rapid changes in steam demand will not reduce steam quality. To affect either of the above, use modulating versus on-off valves at steam-use points. Add boiler feedwater with modulating versus on-off controls.
73 Indirect method 80 Direct or fuel-to-steam efficiency. 87 Boiler management and control. 87 Typical instrumentation for boiler management 90 Contamination of condensate 90 Boiler level controls 90 Hotwell temperature 91 Hotwell level 91 Total dissolved solids (TDS) 93 The European boiler market.
The capacity of the boiler to have steam, as well as water is sufficient. Generally, the liquids are stored in the boiler for generating steam by burning the fuels or applying the heat energy at different conditions of pressure based on the size of the vessel as well as specifications.
No. 76, Xin Da Road, Zhou tie Town, Yixing, Wuxi, China
0086-510-68530066, +86-13506151292Get Latest Price
Copyright © 2020.Zhongzheng Boiler Co., ltd. All rights reserved.