Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Available Fuel: Nature gas, coke oven gas, biogas, methanol, liquid propane gas, diesel, heavy oil, light oil, crude oil, etc.
Available Industries: Heat supplying, chemical, food, textile, printing and dyeing, cigarettes and tobacco, fodder, pharmacy, building materials, brewery, rubber, hospital etc.
WNS series horizontal internal combustion boiler is a boiler shell type 3 passes wetback oil/gas fired boiler. After fuel is being atomized by burner, flame is full of the wave furnace and transfer heat via furnace wall, this is 1st pass; the high temperature smoke is collected in reversal chamber and then enters 2nd pass which is grooved tubes bundle area; after heat convection, air temperature gradually falls and goes to front smoke box and turn to 3rd pass, which is smooth tubes bundle area, and then enters chimney passing back smoke box and exhausted to the atmosphere.
1. Digitized manufacture
The key part such as material cutting, rolling, drilling are proceeded by advanced CNC machining process to reduce the assemble stress and extend boiler working lifetime.
The front and back smoke chamber plates are cut by CNC plasma cutting machine and looks tidy and beautiful.
2.Easy operation and maintenance
Fully automatically operating, with automatically adjustment and protection of burning, water level, temperature and steam pressure.
3. Longer working life
Smoke tube and tube sheet connection is expanded first to eliminate the gap between them, then adopt automatic argon arc welding to relief the stress and expand boilers working life.
Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will have 100% radiographic inspection.
Fin tube us ND steel or stainless-steel material which avoid low temperature corrosion.
Inspection procedure point is set up to guarantee the sequence of expanding and welding, avoid cracking of the tube sheet holes.
4. Less fuel consumption
High quality aluminum silicate fiber is used with fire clay insulation, to control the boiler body temperature below 45℃ to control heat lost.
Sufficient steam storage room and heating area makes boiler to generate high quality steam and high thermal power.
Condenser is added to reuse the waste heat of the exhausted smoke to increase feeding water’s temperature and reduce emission temperature, which can increase the thermal efficiency above 98% and save operating cost.
This Boiler House Block of the Steam and Condensate Loop will concentrate on the design and contents of the boiler house, and the applications within it. A well designed, operated and maintained boiler house is the heart of an efficient steam plant. However, a number of obstacles can prevent this ideal.
Start studying Unit 12 - Chapter 51 - Introduction to Boilers. Learn vocabulary, terms, and more with flashcards, games, and other study tools.
Sep 08, 2017· What is a Boiler: Introduction to Boilers. Sailorinsight September 8, 2017 January 12, 2018 EXAMS, Marine Engines 0. Types of boilers: Water tube type: this type of boiler is used for high pressure, high temperature, high capacity steam applications eg …
May 18, 2013· Boiler Introduction 1. Boiler-A ‘Boiler’ means a pressure vessel in which steam is generatedfor use external to itself by application of heat which is whollyor partly under pressure when steam is shut off but does notinclude a pressure vessel(1) With Capacity less than 25 ltrs (such capacity beingmeasured from the feed check valve to
Black Liquor Recovery Boilers - An Introduction. David Parrish Factory Mutual Research Corp. Winter 1998 . Category: Operations . Summary: The following article is a part of National Board Classic Series and it was published in the National Board BULLETIN. (4 printed pages)
File Size: 1MB Sep 30, 2014· A Brief Introduction to Boilers 1. Brief Introduction 1 SatyakamMohapatra Engineer(Mechanical) Monnet Power Company Ltd 2. BOILER In General, A boiler is a closed pressure vessel strongly constructed of steel or iron where water is converted to steam by application of heat.
Now that the basic structure of a boiler has been explained, boiler fittings (fig. 1-6) and the operation or function of various devices, such as controls, valves, and try cocks, must be presented. A sufficient number of essential boiler fittings and accessories are discussed in this section to …
an introduction to treatment of steam boiler water j. paul guyer, p.e., r.a. contents 1. steam boiler systems 2. boiler water treatment and control 3. developing a steam boiler system water treatment program 4. chemical requirements for boiler start-up 5. chemical requirements for boiler layup 6. commonly asked questions and answers on
One consideration is the introduction of feedwater to the boiler. The pump used to charge the boiler must be able to overcome the boiler's operating pressure, else water will not flow. As a superheated boiler is usually operated at high pressure, the corresponding feedwater pressure must be even higher, demanding a more robust pump design.
No. 76, Xin Da Road, Zhou tie Town, Yixing, Wuxi, China
0086-510-68530066, +86-13506151292Get Latest Price
Copyright © 2020.Zhongzheng Boiler Co., ltd. All rights reserved.